Gilbert, AZ Heating and Air Conditioning Services
Morehart Air Conditioning & Heating provides heater and air conditioning repair, installation and services in Gilbert, AZ and surrounding areas.
Check out what some of our customers are saying about Morehart Air Conditioning & Heating services.
for Gilbert, AZ
In Gilbert, near East Sandcastle Court and North Sailors Way performing seasonal preventative maintenance on an Amana heat pump. Cycled system on in cool and heat. Checked volt and amp draws, and all are within manufacturer specifications. Air scrubber light is out; need to replace scrubber cell. Cleaned and tightened electrical connections. Changed return air filter and checked splits. Picked up air scrubber cell at Ferguson and installed.
In Gilbert, near East Ivanhoe Street and South Seton Avenue installing a new control board. Disconnected high and low voltage as well as harness wiring. Re mounted new board to brackets and rewired control board. Tested system in heating and cooling and upon departure, unit is working properly and within manufacturer specifications.
In Gilbert, near East Ivanhoe Street and South Higley Road performing a diagnostic on a Goodman condenser. Upon arrival, system was operational and working properly. I would recommend replacing gas furnace control board due to it sending intermittent signals to run condenser.
In Gilbert, near E Walnut Road and South Granite Street performing a diagnostic on a Trane condenser. Upon arrival, found that compressor is inoperable and fan was solely running. Replaced run capacitor and upon departure, everything is in working order.
In Gilbert, near East Megan Street and South Banning Street performing a diagnostic on a Goodman condenser. Noticed split system inoperable. At furnace, found low voltage fuse shorted due to exposed low voltage wire. Replaced fuse and fixed wiring. Unit is working properly and within manufacturer specifications upon departure.
In Gilbert, AZ: ESTIMATE- Provided homeowner with an estimate on installing mini split. Pending approval from homeowner. Service complete.
In Gilbert, AZ: Estimate: Morehart AC to install and furnish 2, three ton gas split systems. To include new secondary pan, wet switches, thermostats, disconnect box, whip kits, flue piping, and gas flex line. To hook up to existing high volt, low volt. ducting, and line set.
In Gilbert, AZ: Upon arrival, cycled units into cooling mode. Took temperature readings from supply and return. Homeowner declined filter replacement or being left with intake filters. At units, cleaned and tightened electrical connections. Took volts and amp draws from components. Checked Freon levels with super heat and subcool. Upon departure, units are working properly and within manufacturer specifications.
In Gilbert, AZ: Upon arrival, cycled unit into cooling mode. At the outdoor unit, noticed compressor inoperable. After diagnosis, found capacitor out of spec. Replaced 80/5 capacitor. Upon departure, unit is working properly and within specs.
In Gilbert, AZ: UPON ARRIVAL CYCLED UNIT INTO COOLING MODE. REPLACED INTAKE FILTERS AND ALSO TOOK TEMPERATURE READINGS FROM SUPPLY AND RETURN. CLEANED AND TIGHTENED ELECTRICAL CONNECTIONS. TOOK VOLTS AND AMP DRAWS. CHECKED FREON LEVELS AND CAPACITORS. UPON DEPARTURE UNIT WORKING PROPERLY AND WITHIN SPEC.