Wickenburg, AZ Heating and Air Conditioning Services
Morehart Air Conditioning & Heating provides heater and air conditioning repair, installation and services in Wickenburg, AZ and surrounding areas.
Check out what some of our customers are saying about Morehart Air Conditioning & Heating services.
for Wickenburg, AZ
In Wickenburg, near West Wickenburg Way and North Vulture Mine Road performing a diagnostic on a Carrier package heat pump. Found that the run capacitor was bad; installed new run capacitor on blower motor. System is running within manufacturer specifications upon departure.
In Wickenburg, near West Wickenburg Way and North Vulture Mine Road performing a diagnostic on a commercial Carrier package heat pump. Upon arrival, found thermostat to be blank due to blown fuse; capacitor blown apart and motor grounded out. Installed new 1/4 Horse 1075 460 volt motor and new 7.5/440 run capacitor with new fuse, and system is now running properly and within manufacturer specifications.
In Wickenburg, AZ: Checked furnace and coil in the garage. Supply is sealed very well and clean. Gas line is tight and sealed. PVC flue piping is correct and glued. Drain line for furnace and coil are plumbed and glued properly. Cycled furnace on, all working properly. Cycled cooling. Checked condenser, hooked up gauges; pressures are set proper. Suction 130 Liquid 357. Disconnect installed with new whip and proper. Install looks very good with no issues. Removed program off thermostat. Customer just wants easy. Completed QC.
Beautiful day for services! In Wickenburg performing preventative maintenance on 4 Amana systems!